Extra Low Profile Fan Coil Units with EC fan motors.
Up to 1,600 Litres/Sec.
The SLIMtherm TM range of Fan Coil Units combines the benefits of a quality double skin casing construction and an extra low profile design. Units are also available in horizontal configurations.
SLIMtherm units in a vertical configuration are designed to minimize the plant room space needed for installation. The compact dimensions of the vertically configured SLIMtherm units makes them ideal for projects where plant room space is restricted.
The units are constructed with 25mm thick insulated panels that are fitted with the revolutionary FCU CLIP ‘n’ LOCK fastening system. This airtight system includes a synthetic cord and aluminium capping that gives the unit a strong, rigid structure and allows the panels to be removed easily for maintenance and cleaning. The high quality modular casing construction achieves the highest degree of air tightness, rating “L1”, as defined in BS EN 1886:2007.
SLIMtherm units include high efficiency EC plug fans that can be controlled by MODBUS or 0-10V signal and run independently or integrated into most building management systems. The EC fans can be easily accessed for maintenance or replacement by removing an FCU CLIP ‘n’ LOCK side panel.
Units incorporate the unique FCU CLIP ‘n’ LOCK system where the removable casing panels clip into a continuous aluminium locking strip with an EPDM closed cell foam underseal. The locking strip is secured into position with a continuous synthetic cord, forming an airtight seal. Casing includes double skin, 25mm thick, polyurethane-filled removable panels. The unit case has a Class L1 leakage rating.
Each unit is pre-fitted with G4-rated, 25mm flat panel filters mounted on an external slide rail. The condensate tray is of a non-ponding design manufactured from grade 304 stainless steel. Units incorporate multiple, high efficiency single phase EC plug fans. The number of fans varies depending on the model.
Integral thermal overload protection is supplied as standard.
Protection will not prevent fans from functioning in fire mode as required by AS/NZS1668.1:2015.
The Fan Coil Units shall be of the SLIMtherm series as designed by Fantech and be of the model numbers shown on the schedule drawing.
Units shall incorporate a modular, aluminium frame construction with double skin, 25mm thick, polyurethane filled panels that achieve the highest degree of air tightness rating “L1”, as defined in BS EN 1886:2007. Panels shall have zero ozone depleting potential (0% ODP).
Unit casings shall incorporate AHU CLIP ‘n’ LOCK removable panels that are sealed air tight by the use of a continuous clip in aluminium locking strip with a continuous EPDM closed cell foam underseal. The panels are locked into the strip with a continuous synthetic cord. The panels shall be removable without the need to remove screws or fasteners. Cooling and heating capacities and external static pressures shall be as shown on the schedule.
Units shall be complete with filter plenums with filter frames fitted. Filter plenums shall have the same construction as the Fan Coil Unit.
Fans shall be backward-curved, centrifugal type, driven by EC motors with an IP54 rating. Fan motors shall be pre-wired to an external terminal box.
Units shall use G4 or 50mm filters.
|0.5 x 1
|2.4 x 1
|0.5 x 2
|2.3 x 2
|0.5 x 2
|2.3 x 2
|0.5 x 3
|2.3 x 3
|0.5 x 3
|2.3 x 3